Interested in this product?
Send us a request and we will contact youOur Certificates
Standart: VDE 0276 part 603
Description: Cu conductors • PVC insulation • PVC sheath
NYY is used in power plants industrial and switching installations, in secondary distribution networks and other.These cables are preferentially used in outdoor applications, for indoor instalations, in the open air, underground and in water where mechanical damage is not anticipated. Note Other core configuration and special constructions manufactured upon request. Cables with same construction may produced according to IEC 60502.
Multiple core black with number mark on cores or black with number mark on cores and yellow/green core in the outer cover.
|Construction||According to VDE 0276 part 603||Conductor resistance at 20° C||According to VDE 0295
class 1 or 2 (IEC 60228)
|Conductor||solid or multi-strand Cu wires class 1 or 2 acc. VDE 0295 (IEC 60228)||Max. conductor temperature||+70° C|
|Insulation||PVC compaund||Max. short circuit temperature||+160° C , not more than 5 sec|
|Core identification||according to VDE 0293||Rated voltage Uo/U||0.6/1 kV|
|Inner sheath||filling compound or tapes||Test voltage||AC – 4 kV 50 Hz|
|Sheath||PVC compaund||Bending radius
15 cable diameter
12 cable diameter
|Color||black||Flame test||VDE 0472 part 804 class B
(IEC 332 part 1)